|Place of Origin:||China|
|Certification:||ISO SGS CE GB|
|Minimum Order Quantity:||1|
|Price:||usd 5000-98000 set|
|Packaging Details:||1.Package: Regular package or nut package; 2.Transportation: By land or by sea , it depends on the exporting areas.|
|Delivery Time:||1-20 working days|
|Payment Terms:||L/C, T/T, MoneyGram|
|Supply Ability:||5000 set per year|
|Product Name:||1-20ton DZL Coal Biomass Fuel Industrial Boiler Steam||Rated Steam Capacity:||1t/h-20t/h|
|Structure:||Water And Fire Tube||Rated Pressure:||1.25 Mpa|
|Rated Steam Temperature:||184 ℃||Design Fuel:||Coal,Biomass|
|Grate:||Chain Grate And Moving Grate|
horizontal fire tube boiler,
steam boiler machine
DZL series biomass boiler is a horizontal three-way water fire tube boiler. Arrange the threaded pipe in the drum, on both sides have the water wall tube, front and back arch with a new type of energy-saving furnace arch, the use of light small scale chain grate is more conducive to the combustion of biomass fuels, with a blower, induced draft fan for mechanical ventilation, and equipped with a slag machine to achieve automatic slag.
The fuel from the coal bucket fell to the grate, enter into the furnace for combustion, the flame after the back arch refraction upward through the body both sides burning chamber turn to the front smoke box, and then by the front smoke box to the threaded pipe in inside of the drum, after through the back smoke box into the economizer, and then by the induced draft fan pump the smoke into the atmosphere through the chimney flue.
1. By pulling the partial ascension pipe on both sides of the heads into the furnace, and then lead into drum side’s bottom and supplementing with the bottom of the drum to form the roof heating surface, the new furnace structure has successfully solved the bottom of the drum directly by the high temperature flame radiation, to avoid the "drum package" defects.
2. Two wings smoke flue’s design,tom make the smoke flow into front smoke box smoothly and the same tube temperature as before to avoid the temperature stress and produce tube plate cracks.
3. The drum with a single return thread pipe, to strengthen the heat transfer effect, while the threaded pipe with self-cleaning function, to avoid the ash deposits inside the pipe.
4. Boiler front and back arch adopt support the water wall tube as support ‘s overall casting structure, then the formation of permanent arch. The back arch is low and long, the exit section is anti-tilt, the front arch angle 45 °,match the back arch, forming a clear inverted "α" flame, which is conducive to low-grade coal combustion and has good coal adaptability .
5. Grate lateral sealing structure design is advanced and reasonable, avoiding the lateral sealing card grate and the grate both sides uneven wind to cause the defects of burning out the side seal. 4t / h and less then 4t boiler adopts side seal cold angle iron plate structure, above 6t / h boiler adopts contact-type lateral sealing structure.
6. Under the grate have the independent adjustment wind chamber, from both sides inlet air; Using new crank arm screw adjusting structure, so that the air ventilation section ratio reaches 100%, flexible adjustment, ventilation uniform.Push-pull type gate segment soot cleaning device, gate segment adopts heat-resisting cast iron with seal structure, thus effectively preventing secondary combustion deformation and grate air leakage.
Rated Steam Pressure
Feed Water Temperature
We promise every set of machine with the top quality and best after-sales service as followings :
(A)The boiler body guarantee is one years, for accessories three years
(B)During the guarantee period , if the main body defective or broken without wrong operating , we must replace the parts for free or prepare the spare-parts for free.
(C)We should provide boiler technical service and operation guidance for whole life long.
(D)Regarding to the installation and training , the buyer should take all the correlative charges (accommodation and food , round -trip tickets)
Packing and shipping
1. When transport, the boiler body and large auxiliary equipments (platform, chimney, economizer, etc ) are nude packed or tied up.
2. the smaller auxiliary equipments are encased by using the strong intensity wooden or plywood box.
3. The products could be transported by ship and train, customers could designate the ports.
4. If necessary, the small auxiliaries could be transported by air.
Before the Quotation Please Confirm the following parameters first, then we can recommend right boiler model for you with good price.
Contact Person: info